Address: Hong Sheng Jie West District of Liaoning city of Yingkou province No. 33
Lamp: generally refers to a new type of lighting device 15 meters above the conical steel pole and high power combined lamp bracket. The utility model is composed of a lamp cap, an internal lamp, an electric rod and a base part. Lamp holder can be based on user requirements, the surrounding environment, lighting needs specific; interior lamps are mostly composed of floodlights and cast light, light source using NG400 high pressure sodium lamp, lighting radius of 60 meters. The rod body is usually a pyramid shaped structure with a steel plate and a height of 15 - 40 meters.
High pole lamp
Lamp holder, interior lamp electrical
Freight yard, highway, stadium, overpass, etc.
2 use place
5 lifting principle
1 configuration editor
1 pole eight edges and twelve edges and eighteen pyramid shaped rod body is made of high strength, high quality steel plate after cutting, bending, automatic welding, the general height of 25, 30, 35, 40 specifications, the maximum wind resistance design of up to 60 meters / second, each consisting of specifications from 3 to 4 is inserted. With the flange steel chassis, diameter of 1 meters to 1.2 meters, the thickness of 30 mm to 40 m M.
2 in the functional framework, but also to decorative materials mainly to steel, steel pipe, lamp post, lamp plate by hot dip galvanizing.
3 electric lifting system is composed of electric motor, winch, three sets of hot dip galvanized steel wire rope and cable. Lamp post installed in the body, the lifting speed of 3 to 5 meters per minute.
The 4 guiding and unloading system is composed of a guide wheel and a guide arm, so as to ensure that the lamp plate does not move transversely during the lifting process.
5 lighting electrical system is designed to be 6 - 24 - W - 1000 W (white light), light, flood light, computer time controller can automatically control the switch light time and part of the lighting or full lighting,
6 lightning protection system: the top of the lamp is equipped with a 1.5 meter long lightning rod, the underground foundation of the installation of 1 meters of ground wire and ground bolts and 1.
2 use site editor
Use lamp: the city square, station, wharf, warehouse, highway, stadium, overpass.
3 category editor
Generally can be divided into lifting and non lifting. The height of the lifting main rod is generally 18 meters above, the electric lifting operation is convenient, and the lamp disc can be automatically taken off and hung up after the lamp plate rises to the working position.
Lift type high pole lamp with two types of manual and electric lift control mode, the lamp can safely down to 2.5 meters from the ground, convenient maintenance. Manual remote control device lead out of the length of 10 meters, the operator at the remote control of 5 meters of the lifting of the lamp disc, so as to ensure the operator's personal safety. Lift type high pole lamp is also equipped with a spare cable, when the lamp fell to the lowest position, the cable is plugged into the socket of the electric control system, the other end is inserted into the lamp box on the inside, so you can directly supply power to the lamp, lamp maintenance.
Seal level lift type high pole lamp lamp for all IP65 international standards, to prevent dust and rainwater immersion, ensure the service life of the bulb. The material of the lamp is generally made of aluminum alloy plate and stainless steel with good corrosion resistance.
The lamp we often say, in fact, is based on the use of different occasions, according to different classification of the lamp and it is different. For example, dock, dock called pole lamp, square, square is named after the high pole lamp, high pole lamp port, airport, explosion-proof lamp, stainless steel lamp etc.. Usually think the lamppost is more than 15 meters, high pole lamp, 15-40 meters, commonly used is 15 meters, 18 meters, 20 meters, 25 meters, 30 meters of the 5 most common specifications. The other is generally highly specific design requirements of customers, this is what we often say that divided according to the height of pole.
4 install edit
1 carefully check all the components according to the loading and packing list.
2 check whether the component is damaged, bent, twisted, zinc layer is damaged.
3 the marks on each rod indicate the type of the rod, the order number, the number of segments. With the rod body weight with the brush on the rod body. Compared with the correct delivery of the goods, crane hoisting capacity is sufficient.
4 according to the maximum and minimum sleeve length provided on the drawing, marking on the rod body for the use of socket.
1 each splice to provide a set of length, but due to the manufacture, installation error and physical factors, such as the existence of the sleeve length change, the maximum length of the sleeve and the minimum sleeve length.
2 in order to facilitate the installation, may need to lubricate the surface. Be careful not to use lubricating oil to prevent leakage and contamination of the rod body.
3 sets of joints to be applied at both ends of the necessary force to obtain a tight sleeve.
5 principles of editing
A rectangular cavity at the bottom of the lifting pole, in addition to the control system of electrical installation is installed motor lifting system. The electric control system is installed in the lamp post, which can avoid the trouble caused by the bad outdoor environment. Electrical control system with a variety of circuit overload protection device. The copper conductor is widely used in the circuit of the system, so as to ensure the good contact of the electrical connection. Lifting system of lift type high pole lamp is through the motor (electromagnetic brake) worm reducer, safety coupling, main wire rope, wire rope, rope side and moving pulley components such as driving lamp up
High pole lamp
Drop. The worm gear reducer has the advantages of strong self-locking capability, compact transmission and large transmission ratio